Cabrillo has been servicing and repairing the plumbing, heating and cooling systems of homes and businesses in Redwood City CA since 1961.
Call us now at: 415-821-0560 or check out why your neighbors think of us as the experts in repairing, replacing and servicing plumbing and hvac systems in Redwood City CA.
for Redwood City, CA
Exceptional service ...5 stars in all areas!
Frank - Redwood City, CA 94061
First... the job was completed on time and perfectly. Frank and his partner were courteous and very responsive to our questions. Could not be more satisfied.
Jocelyne - Redwood City, CA 94061
Patrick was quick and efficient
Happy and informed customer!
Omar - Redwood City, CA 94065
Friendly and fast service!
Katie - Redwood City, CA 94062
Excellent Service, helpful advice. On schedule.
Michael - Redwood City, CA 94065
Explained the 2 options available to us. Assisted with great advice to help us make the right decision. Took the time to explain the work involved and then completed the job very efficiently. Clean up was spotless.
Katie - Redwood City, CA 94062
Tony was great. Super professional and fast.
Very good service
Jo - Redwood City, CA 94062
We've had two service reps come to our home within the last week for two different reasons, one a clogged drain causing a back up of sludge into our shower and another for routine furnace inspection that turned up burned wires from a spider's web. In both instances, the service was impeccable. We continue to use Cabrillo because we've come to trust the company and always receive great service.
Plumber replaced angle stop under kitchen sink and installed new water filter faucet.
Plumber installed Grohe comfort series recirculating pump
HVAC technician installed new supply and return air duct work in attic. Duct system had poor air flow due to improperly installed duct work.
Plumber installed two new hose bibbs and washing machine hoses in garage.
Maintenance check up on Carrier furnace.
Maintenance check up on Carrier furnace. Everything working properly at this time
HVAC technician performed annual maintenance on Carrier furnace.
Plumber snaked mainline sewer drain, removed roots from drain. Video inspection of mainline pipe.
Plumber cleared shower stoppage. Hair build up in drain line.
Maintenance check on Bryant furnace and GE water heater. Everything ok at this time.
Plumber installed Toto Drake ADA toilet
Maintenance on Carrier furnace. Replaced 14x24x1 filter. Customers stated no airflow in living room. Found crushed duct in attic. Will provide estimate for duct repair.
Plumber performed camera inspection on main sewer line and found a defect in the pipe under the concrete floor. Also removed blockage in lavatory sink.
Plumber installed customer supplied Moen kitchen faucet with sidespray.
Estimate for air conditioner add on.
Plumber unclogged the kitchen sink
Plumber performed gas leak detection test.
Plumber replaced pilot assembly in water heater
Replaced 17year old water water heater with new 50 gallon water heater installed with new drain pan and expansion tank.
Air conditioning unit not cooling. Charged 1lb R-410A refrigerant. Tested. Trane unit working properly at this time
Plumber gave estimate for water heater repair or new water heater installation.
Plumber replaced emergency shut off valve for a toilet and replaced the fill valve in the toilet