Cabrillo has been servicing and repairing the plumbing, heating and cooling systems of homes and businesses in San Mateo CA since 1961.
Call us now at: 415-821-0560 or check out why your neighbors think of us as the experts in repairing, replacing and servicing plumbing and hvac systems in San Mateo CA.
for San Mateo, CA
A New Water Heater
Allen - San Mateo, CA 94403
Brian really did an incredible job installing our new water heater. He is very knowledgeable and takes the time to explain everything involved. We would definitely request for his services in the future.
Anna - San Mateo, CA 94402
Dave from Cabrillo is fantastic! Over the past few years, he has helped me replace my water heater and two toilets. He is incredibly professional and polite. I am a very happy customer.
Warren - San Mateo, CA 94403
We got quick help on a Saturday morning. A very pleasant professional plumbing service call. We will use Cabrillo again.
Plumber rebuilt toto toilet.
Plumber cleared main line stoppage with Ridgid drain machine. Pulling and resetting toilet was required from drain access.
Plumber cleared a main sewer stoppage with a hydro jetter
Carrier air conditioner not working. Found defective dual run capacitor. Replaced capacitor and tested. Unit ok at this time
Plumber unclogged sink drain and gave estimate for Grundfos comfort series recirculating system and an estimate for a toto toilet
Plumber installed new toilet handle on old American Standard toilet.
Plumber cleared dishwasher stoppage and secured air gap to kitchen sink.
Plumber cleared clogged kitchen sink.
Plumber unclogged shower and sink
Plumber installed a hand shower
York air conditioning unit had leak in coil. Ordered part and will return to repair
Plumber performed water leak detection.
Plumber repaired a Rheem water heater.
Plumber cleared a stoppage in the kitchen drain
Plumber cleared clogged master shower drain and bath sink drain.
Plumber left estimate for removing and resealing Toto toilet, Kohler faucet repair and shutting building down to install new toilet shut off valve.
Plumber snaked clogged bath tub drain too clear stoppage.
Plumber installed customer supply hand held shower head. Dye tested toilet for water conservation.
Plumber replaced angle stop and supply line under kitchen sink.